NGVAmerica Issues Technical Bulletin – Cold Weather Notice for Natural Gas PRDs
Washington, DC – With the onset of colder temperatures, NGVAmerica today issued a technical bulletin reminding natural gas vehicle (NGV) owners and operators that moisture trapped in pressure relief devices (PRDs) and in PRD vent lines can freeze and cause damage. This reminder becomes especially important during the winter months when freezing temperatures are common.
NGVAmerica’s Technology & Development Committee advises that ice damage in PRDs and PRD vent lines can result in the following unintended consequences:
- Unexpected activation of the PRD, resulting in the release of the fuel tank contents, PRD leaks, or PRDs not being able to activate.
PRDs are intended to be used as a safety device for NGVs by releasing the natural gas fuel tank contents in the case of a vehicle fire. The location of PRDs can vary, but they are typically located at one or both ends of the NGV fuel tanks. In cases where multiple NGV fuel tanks are used, the PRDs may be in a manifold configuration, typically connected to a vent port.
Incidents have shown that moisture from rainwater and vehicle washes may enter the PRD vent systems through accessible openings. Vent outlets that are open due to missing moisture caps are a very common point of entry for water; however, loose fitting caps can also allow moisture to enter the PRD vent system. Moisture collected in a PRD system can cause PRD internal components to become distorted, resulting in premature PRD activation. This potential failure mode exists on any CNG fuel systems with openings in the vent system but has been most prominent on vehicles with roof mounted PRD systems.
CSA NGV 6.1-2018 Compressed natural gas (CNG) fuel storage and delivery systems for road vehicles will address some of these concerns. NGV manufacturers typically recommend routine inspection of PRD vent systems to verify the integrity of the vent lines and assure that all vent caps are in place. The occurrence of this inspection varies between vehicles. NGV owners and operators are encouraged to consult their vehicle owner’s guide and/or the manufacturer for appropriate inspection procedures. If vent caps are discovered to be missing, or there are other signs of moisture present in the PRD vent system, the owner/operator should contact their vehicle manufacturer immediately for recommended actions.
This NGVAmerica guidance is publicly available and shareable for NGVA members and partners on our website.
NGVAmerica is a national organization of over 200 companies, environmental groups, and government organizations dedicated to the development of a growing, profitable, and sustainable market for vehicles powered by natural gas or biomethane. NGVAmerica member companies produce, distribute, and market natural gas and biomethane across North America, manufacture and service natural gas vehicles, engines, and equipment, and operate fleets powered by clean-burning gaseous fuels. Find out more at: www.ngvamerica.org.
NOTICES AND DISCLAIMER:
NGVAmerica has taken great effort to ensure the accuracy and reliability of the information contained in this document; however, this document is provided “as is” and neither NGVAmerica nor its employees or agents make any representation, warranty or guarantee in connection with this document, express or implied. NGVAmerica and its members companies disclaim liability for any personal injury, property or other damages of any nature whatsoever, whether special, indirect, consequential or compensatory, directly or indirectly resulting from the publication, use of, or reliance on this document. Nothing contained in this document should be viewed as an endorsement or disapproval of any particular service provider or products. The information contained in this document is not intended as legal advice. Questions regarding this document should be sent to: NGVAmerica, 400 N. Capitol St., N.W., Suite 450, Washington, D.C. 20001.